KAN-therm Profil is a complete system designed for building heating and cooling underfloor installations.
For a KAN-therm Profil floor heating pipes are pressed into the upper part of a styrofoam plate provided with a special profile and covered in a plastic layer. This is a wet method of laying a heating system. With 11 mm thick styrofoam plates the KAN-therm Profil System can be applied also for a wall heating.
To mount the KAN-therm Profil System floor or wall heating use:
„Profil“ Styrofoam with profiled tongues to snap-fasten pipes. With such a design of styrofoam pipes can be laid and fastened directly without using additional fasteners. Styrofoam is available in sheets of a thickness of 11 - 30 mm,
polyethylene pipes PE-Xc, PE-RT, PE-RT Blue Floor or multi-layer PE-RT/Al/PE-HD, PE-RT/Al/PE-RT pipes - Ø16 - Ø18 mm,
edge band with incision or with an incision and a foil apron,
plasticizer BETOKAN or BETOKAN Plus for concrete,
distributors and pumping groups for surface heating,
installation boxes: surface mounted, concealed or for cladding with glazed tiles.
Assembly of KAN-therm Profil System floor heating:
1. The first step is to lay the wall along construction partitions of a room.
2. Next we lay the styrofoam with foil so that it overlaps on the adjacent styrofoam sheets.
3. The next step is laying pipes by pressing them into a profiled upper part of the Profil plates.
4. This method of fastening pipes is fast and sure and pipes are laid according to a designed spacing.
After laying pipes, connecting them to a distributor and after pressure-testing them you can start pouring a floor with concrete with the addition of the BETOKAN or BETOKAN Plus plasticizer (depending on the required floor thickness).